Goodman Sanitation Services
We Offer Septic Real Estate Evaluations - Click Here to Learn More
The most common water waste systems used in rural areas is the septic tank-soil absorption systems. The septic tank removes settable and floatable solids from the wastewater, and the soil absorption field filters and treats the clarified septic tank effluent. Removing the solids from the wastewater protects the soil absorption systems from clogging and premature failure. In addition to removing solids, the septic tank also stores the settled portion and permits digestion of a portion of those solids.
The septic tank removes solids by holding wastewater in the tank, which allows the solids to settle and scum to rise to the top. To accomplish this, wastewater should be held in the tank for at least 24 hours. Up to 50 percent of the solids retained in the tank decompose. The remaining solids accumulate in the tank. Biological and chemical additives are not needed to aid or accelerate settling or decomposition.
As the septic systems is used, sludge continues to accumulate in the bottom of the septic tank. Properly designed tanks have enough surface space for up to three years safe accumulation of sludge. When the sludge level increases, more solids beyond this point, sewage has inadequate time in the tank to allow proper settling before leaving the tank. As the sludge level increases, more solids escape into the absorption area. If too much sludge accumulates, no settling occurs before the sewage slows to the soil absorption area. To prevent this, the settled solids in the tank must be pumped periodically. The material pumped out of the tank is known as “septage.”
The frequency of pumping depends on several factors:
- Capacity of septic tank
- Flow of wastewater
- Volume of solids in wastewater (more solids if garbage disposal is used)
Table 1 gives the estimated pumping frequencies according to septic tank capacity and household size. The frequencies were calculated to provide a minimum of 24 hours of wastewater retention assuming 50 percent digestion of the retained solids.
In Oregon, a 1,000-gallon tank is used for a home with three bedrooms. If six people reside in 3-bedroom house, the tank should be pumped every 1.5 years. If the same systems serves a family of two, the tank would be ready for pumping every 5.9 years. Systems installed before the current rules and regulations may have smaller septic tanks. As shown in table 1, some tanks may need to be pumped more often than once a year.
It is important to note that the soil absorption field will not fail immediately when a full tank is not pumped. However, the septic tank is no longer protecting the soil absorption field from solids. Continued neglect will result in failure of the soil absorption field and it may need to be replaced. In some cases, replacement of the absorption area may not be possible due to site limitations.
Cleaning The Tank
Septic tank pump and haul contractors can empty and clean your tank. It is a good idea to supervise cleaning to ensure that is done properly. To extract all the material from the tank, the scum layer must be broken up and the sludge layer stirred up into a liquid portion of the tank (see Figure 1). This is usually done by alternately siphoning liquid from the tank and re-injecting in into the tank. The septic tank should be pumped out through the large central manhole, not the baffle inspection ports. Pumping out a tank through the baffle inspection ports can damage the baffles.
Before closing the tank, check the condition of the baffles. If they are missing or deteriorated, replace them with sanitary tees. Never enter a septic tank. Any work to replace the baffles or repair the tank should be made from the outside. The septic tank produces toxic gases which can kill a person in a matter of minutes. When working on a tank from the outside make sure the areas are well ventilated and someone is standing by. Never go into a septic tank to retrieve someone who was overcome by toxic gases or the lack of oxygen without a self contained breathing apparatus (SCBA). If a SCBA is not available, the best thing to do is call for emergency services and put a fan at the top of the tank to blow in fresh air. To facilitate cleaning and inspection, install risers from the central manhole and inspection ports to the surface or near the surface before burying the tank. Also mark the location of the tank so these openings can be easily located.
The septic tank is only one part of an on-site wastewater systems. It is designed to remove solids to protect the soil absorption systems, store, and provide for the digestion of a portion of those solids. . Biological and chemical additives are not needed to aid or accelerate settling or decomposition. Garbage disposals are not recommended, because they impose an additional solids load on the systems. Solids must be removed periodically from the septic tank to keep them from entering the soil absorption systems. For a properly designed septic tank, the tank should be inspected and pumped every 1 to 5 years.
Note: More frequent pumping needed if garbage disposal is used
Figure 1. CROSS SECTION OF A SEPTIC TANK WITH (optional) EFFLUENT FILTER
Extension Services, Oregon State University, Corvallis, O.E. Smith, director.
This publication was produced and distributed in furtherance of the Acts of Congress of May 8 and June 30, 1914. Extension work is a cooperative program of Oregon State University, the U.S. Department of Agriculture, and Oregon counties.
Oregon State University Extension Service offers educational programs, activities, and materials – without regard to race, color, national origin, sex, age, or disability – as required by Title VI of the Civil Rights Act of 1964, Tax IX of the Education Amendments of 1972, and Section 504 of the Rehabilitation Act of 1973. Oregon State University Extension Service is an Equal Opportunity Employer.
NEW OREGON DEQ GUIDELINES
There are inspections for homeowners who want to remodel their homes with additions to the house or property.
There are inspections for hardship cases for homeowners who want to add a mobile home to the property and attach to the existing septic systems.
There is the "time of transfer" inspection / evaluation when the homeowner is selling the property.
Each of these inspections require that the tank be uncovered, the distribution box(es) be uncovered, that there is an amount of water introduced to the tank, to watch the contents flow to the distribution box and be accepted by a "thirsty" drainfield, to pump the tank and note any deficiencies.
To do an inspection on any and all pump vault components and panels along with electrical connections. To provide a detailed plot plan meeting all DEQ Specified requirements with all DEQ forms filled in completely with our technicians "certified" number and identification on the reports.
Should any repairs be needed to help bring your systems "up to date" with compliance codes. We will outline the repairs and the cost and schedule an appointment for you. This gives you time to make an informed decision, ask questions, research websites, or ask for comparison bids for repair or work on fitting the repairs into your budget.
Your septic systems is the second biggest investment, next to your home and Goodman Sanitation will be considerate on how you spend your money.